Best Defense Provides Complete Life-Safety Solutions for Wisconsin Care Facilities
We're proud to provide complete life-safety solutions for Wisconsin community-based residential facilities, assisted living facilities, adult daycares, daycare facilities, and nursing homes. Best Defense can install sprinkler systems, fire alarms, door alarms, delayed egress locking systems, camera systems, and nurse calls for these facilities.
We're familiar with all the codes relevant to CBRF, daycare, and nursing home fire alarm requirements in Wisconsin. We can assist you in designing a fire alarm system or sprinkler system to meet code requirements and will provide and submit to the State of Wisconsin a comprehensive plan review package for your installation.
In particular, Wisconsin CBRF's have unique and specific fire alarm codes. Wisconsin Statutes, Section 50.035 requires all CBRF's to have a low voltage interconnected fire alarm and Wisconsin Administrative Code DHS 83.48 spells out the specific requirements for detector placement and inspection. Each of these codes require the systems to be installed to NFPA72 installation standards.
Best Defense also provides annual fire alarm inspections and fire alarm sensitivity testing to meet DHS 83 and NFPA72 testing requirements. We offer a comprehensive set of testing tools including barcoding for each of your devices to track the inspection and hi-tech smoke detector sensitivity testing equipment.
Contact us for all of your fire alarm needs at firstname.lastname@example.org or call us at 800-237-8389.
DHS 83.48 – Fire Protection Systems – Fire Alarm Requirements
- INTERCONNECTED SMOKE AND HEAT DETECTION SYSTEM.
(a) Except as provided under sub. (2), the CBRF shall have an interconnected smoke detection system pursuant to s. 50.035 (2), Stats., and shall have an interconnected heat detection system to protect the entire CBRF so that if any detector is activated, an alarm audible throughout the building will be triggered.
(b) Smoke and heat detectors shall be installed and maintained in accordance with NFPA 72 National Fire Alarm Code and the manufacturer’s recommendation. Smoke detectors powered by the CBRF’s electrical system shall be tested by CBRF personnel according to manufacturer’s recommendation, but not less than once every other month. CBRFs shall maintain documentation of tests and maintenance of the detection system.
(c) A CBRF shall receive approval from the department as required under s. 50.035 (2) (b), Stats., and s. DHS 83.63 (2) before installing a smoke and heat detection system.
- RADIO−TRANSMITTING SMOKE AND HEAT DETECTION SYSTEM.
A small CBRF may use an Underwriters Laboratories listed radio−transmitting detection system that triggers an alarm audible throughout the building and that is properly safeguarded against deactivation.
(a) After the first year following installation, fire detection systems shall be inspected, cleaned and tested annually by certified or trained and qualified personnel in accordance with the specifications in NFPA 72 and the manufacturer’s specifications and procedures.
(b) Sensitivity testing shall be performed at intervals in accordance with NFPA 72.
(c) All smoke and heat detectors suspected of exposure to a fire condition shall be inspected, cleaned and tested by a certified or trained and qualified person within 5 days after each exposure in accordance with the specifications in NFPA 72 and the manufacturer’s specifications and procedures. Each detector shall operate within the manufacturer’s intended response or it shall be replaced within 10 days after exposure to a fire condition.
Pursuant to s. 50.035 (2) (b), Stats., all facilities shall have at least one smoke detector located at each of the following locations:
(a) At the top of every open stairway.
(b) On the hallway side of every enclosed stairway on each floor level.
(c) Spaced not more than 30 feet apart in every corridor, and not further than 15 feet from any wall or in accordance with the manufacturer’s separation specifications.
(d) In each common use room, including a living room, dining room, family room, lounge and recreation room, but excluding a kitchen, bathroom or laundry room.
(e) In each bedroom.
(f) In all non−resident living areas, except the furnace, bathroom,kitchen and laundry room.
(g) Additional smoke detectors shall be located where wall projections from the ceiling or lintels exceed 8 inches.
(h) In the basement, or in each room of the basement except a furnace or laundry room.
- CONNECTION AND ACTIVATION.
Smoke detectors in or near the living room of an apartment and smoke detectors in the bedrooms of an apartment shall be either connected to the main alarm system or to a separate annunciator on a panel. If a separate annunciator on a panel is used, there shall be an effective electronic means of notifying employees anywhere in the CBRF that a detector has been activated. Smoke detectors under this subsection shall activate an alarm in all of the resident bedrooms and the apartment.
- SPECIFIC LOCATIONS FOR HEAT DETECTORS.
CBRFs shall have at least one heat detector integrated with the smoke detection system at all of the following locations or in accordance with the heat detector manufacturer’s specifications:
(b) Attached garage.
(c) All enclosed compartments of the attic.
(d) Furnace room.
(e) Laundry room.
- SPECIAL EQUIPMENT FOR PERSONS WITH IMPAIRED HEARING OR VISION.
(a) Notification. If any resident with impaired hearing or vision is unable to detect or respond to a fire emergency, the licensee shall ensure the appropriate audio, visual or vibrating notification alarms are installed in the resident’s bedroom, in or near a living room in an apartment, and in each common area used by the resident.
(b) Documentation. The sensory impairment of the resident shall be noted in the resident’s record and communicated to all employees within 3 days after admission or after determination of the impairment is made.History: CR 07−095: cr. Register January 2009 No. 637, eff. 4−1−09.
DHS 83.43 – Fire Protection Systems – Fire Sprinkler Requirements
Fire Sprinkler Requirements
(8) SPRINKLER SYSTEMS. (a) Types. A CBRF shall have a sprinkler system if required under s. DHS 83.47 (1) (b) or 83.50. The types of sprinkler systems to be used are as follows:
- A complete NFPA 13D residential sprinkler system shall be used in a CBRF licensed for 16 or fewer residents only when each room or compartment in the CBRF requires no more than 2 sprinkler heads. When an NFPA 13D sprinkler system is used it shall have a 30−minute water supply for at least 2 sprinkler heads. Entrance foyers shall have sprinklers. The department may deter-mine an NFPA 13R residential sprinkler system shall be installed in a CBRF with one or more rooms or compartments having an unusually high ceiling, a vaulted ceiling, a ceiling with exposed beams or other design or construction features that inhibit proper water discharge when the square footage of each room or compartment in the CBRF would ordinarily allow an NFPA 13D sprinkler system.
- A complete NFPA 13R residential sprinkler system shall be used in a CBRF licensed for 16 or fewer residents when one or more rooms or compartments in the CBRF require more than 2 sprinkler heads and not more than 4 sprinkler heads. A fire department connection is not required for an NFPA 13R sprinkler system.
- A complete NFPA 13 automatic sprinkler system shall be used in a CBRF licensed for more than 16 residents.
- All sprinkler systems under subds. 1. to 3. installed after January 1, 1997, shall be equipped with residential sprinkler heads in all bedrooms, apartments, all other habitable rooms and corridors.
- All large facilities initially licensed on or after January 1, 1997, shall be protected by a complete automatic sprinkler system, except a class AA CBRF that has an equivalent safety system approved by the department.
- All large facilities initially licensed before January 1, 1997, of non−fire resistive construction shall be protected by a complete automatic sprinkler system, except a class AA CBRF that has an equivalent safety system approved by the department. (b) Installation and maintenance.1. All sprinkler systems shall be installed by a state licensed sprinkler contractor. All sprinkler systems shall be maintained, inspected and tested at least annually or at intervals determined by the requirements in NFPA 25.2. In facilities with sprinklers, sprinkler heads shall be placed at the top of each linen or trash chute and in the rooms where the chutes terminates.3. The sprinkler system flow alarm shall be connected to the CBRF’s fire alarm system. (c) Reliable water supply. All sprinkler systems shall have a reliable water supply. If the sprinkler system requires a mechanical device such as a compressor, pump or motor, the device shall be supplied by a reliable source of emergency power in accordance with NFPA 20.
History: CR 07−095: cr. Register January 2009 No. 637, eff. 4−1−09
Our licensed sprinkler fitters have years of experience and will provide you with a professionally designed and serviced system at a fair cost.
Best Defense can affordably assist you in meeting all of the NFPA 25 Inspection and Testing (National Fire Protection Association) requirements for your fire protection system.
Our digital video recorders include remote viewing software that allows you to view live or recorded security video from your computer. You'll be able to view and control your digital video through the internet or over your internal network.
Best Defense is your source for fire extinguisher compliance — ensure your extinguishers are compliant with requirements for testing, inspection, and hydro-testing. Professional service at reasonable rates.
3CX IP Telephone Systems
Best Defense uses 3CX IP servers and Cisco SPA IP telephones — easy to install and maintain, you'll save money with a convenient, effective, robust system.
Best Defense installs fire alarm systems for a wide variety of applications. We can design your system to be fire code compliant and provide a full turn-key installation at an affordable price. Throughout the last 20 years we have installed fire alarms in applications ranging from single family homes to nursing homes with over 600 smoke detectors.
Best Defense Security & Fire Protection, Inc, provides professional sprinkler system installation at a reasonable price. We cover everything from small residential style and small CBRF NFPA 13D sprinkler systems, to larger multifamily NFPA 13R systems, and all the way up to full NFPA 13 systems for businesses, warehouses, manufacturing, and high-rack storage.
Best Defense offers a wide variety of nurse call and emergency call systems for assisted living, skilled care nursing, independent living residential care apartment complexes (RCAC), and hospitals.
Whether your facility is a CBRF assisted living facility, skilled care nursing, or hospital, Best Defense can provide you with a RoamAlert patient wandering system throughout Wisconsin. RoamAlert systems are fully expandable and can start with simple single door installations for as little as $2,000 installed all the way up to complex networkd PC based systems with patient logging and locators.
Delayed Egress Locks allow for the locking of required fire egresses, delaying the exit of people from your building. These locks are frequently installed in assisted living, daycare, nursing home, hospital, and retail environments. Although fire and building codes prevent building owners from locking occupants inside their building, delayed egress locks are allowed in many occupancies to delay the egress of a resident for up to 15 seconds.
Best Defense has installed access control card reader systems for companies throughout Wisconsin including large industrial applications, schools, multi-tenant commercial buildings, apartment buildings and even bars. Our access control systems are intuitive, easy to use and expandable, to control an unlimited number of locations.